W. Tombling Ltd.
How to calculate the heat loss for a structure
To calculate the size of heater(s) required to heat a structure, we need to know:
The difference between the ambient and internal temperatures gives the temperature lift required.
Temperature lift = Internal temp. - ambient temp.
The heat loss for a structure is calculated by taking each surface in turn, calculating its overall area and multiplying by its thermal transmittance co-efficient or ‘U - value’ (see table)
Heat loss through surface = width(m) x length(m) x U value
Note the area of windows and doors should be calculated and deducted from the area of the surface they are in, and their heat loss should be calculated separately.
The total surface heat loss for the structure is the sum of all surface heat losses.
Total surface heat loss = loss for walls + loss for roof + loss for floor + loss for windows + loss for doors
An allowance should be made for heat loss through ventilation, which also includes leaks of air through badly fitting doors, windows, damage to the structures surface etc. Putting a value on this can be very difficult, figures range from 20% to 66% depending on the type and condition of the structure.
Total heat loss = total surface heat loss x allowance for heat loss through ventilation
Finally to calculate the heater size needed, the total heat loss is multiplied by the temperature lift.
Heater size required = total heat loss x temperature lift
Example heat loss calculation (see diagram)Temperature lift = 20 - (-5) = 25 deg. C
Area of roof = 2 x 5.09 x 30 = 305.4 m2
Area of walls = (2x2x30) + 10(2+3) = 180 m2
Area of floor = 30 x 10 = 300 m2
Heat loss through roof = 305.4 x 5.7 = 1740 W
Heat loss through walls = 180 x 2.6 = 468 W
Heat loss through floor = 300 x 0.7 = 210 W
Total surface heat loss = 2418 W
Assuming 20% for heat loss through ventilation
Total heat loss = 1.2 x 2418 = 2901 W
Heater size required = total heat loss x temperature lift = 2901 x 25 = 72525 W
In this example 4 - 20kW Activair Ace electric fan heaters , 5 - 15kW Activair portable heaters or 4- 21kW Activair wall mounted electric heaters are needed.
Calculating heater running costs per hour
Calculating the running cost per hour for an electric heater is straightforward. Electricity is sold by the unit (kWh), multiply this by the heater size in kW.
Running cost per hour = heater size (kW) x unit cost of electricity (kWh)
Estimating annual heater running costs
Annual running costs will be greatly affected by physical and geographical location and prevailing weather conditions from year to year. To calculate approximate running costs heating degree day tables are available for most areas, based on average ambient temperatures over a number of years. (contact your local meteorological office or search the internet for ‘heating degree day table’) Consult the heating degree day table to find the annual figure for the temperature the structure is to be maintained at.
Estimated annual energy requirement (kWh)= total heat loss x 86400 x figure from degree table/3600000
Finally to calculate the annual running cost multiply the estimated annual energy requirement by the unit cost of your electricity.
Annual running cost = annual energy requirement x unit cost of electricityDisclaimer. The above example is greatly simplified. U values of building materials vary and are affected by numerous conditions including the position of the structure, i.e. sheltered, normal or exposed. The above should be considered as an approximate method of calculating heater size and running costs. W. Tombling Ltd. accepts no liability or claim arising from use of this information.
Copyright © 2003/6, W. Tombling Ltd.